Mercury-free UVC disinfection – Asahi Kasei demonstrates how Crystal IS UVC LED technology can be applied to achieve higher disinfection efficiency in water treat- ment than conventional mercury lamp
By : Nata Kesuma | Thursday, October 06 2022 - 21:26 IWST
Asahi Kasei Europe GmbH
INDUSTRY.co.id - New York, Tokyo, and Düsseldorf, 5 October 2022 – Asahi Kasei, a diversified Japanese multinational company, and subsidiary Crystal IS have concluded in a bacterial perfor- mance test, an experimental Klaran™ WR water treatment reactor demonstrated over 75% higher performance than a traditional low pressure mercury lamp system using an equiv- alent power consumption level.
Klaran™ WR experimental water treatment reactor demonstrated over 75% higher perfor- mance than a traditional mercury lamp system in a bacterial performance test.
The Klaran™ WR reactor provides a lighter weight, smaller size, longer lasting and safer alternative to mercury lamps.
Asahi Kasei and Crystal IS advancements in UVC LED technology contribute to sustainability in society and are an important step towards actualizing a mercury-free world.Klaran™ WR is an inline Point of Use (PoU) water treatment reactor (Fig. 1, left) which combines Crystal IS’ UVC LEDs based on aluminum nitride (AlN) substrates (Fig. 1, right), with Asahi Kasei’s R&D capability in the design and application of optics and fluid-dynamics.
While conventional UV water treatment systems have used mercury lamps as a light source, nations around the world adopted stricter regulations after the Minamata Convention on Mercury became effective in 2017, due to the hazards that mercury poses to health and the environment. UVC LEDs have been developed as a mercury-free light source featuring small size, light weight, and flexibility in design. A key milestone speeding the transition to this modern light source is demonstrating that the disinfection performance, power efficiency and value of the new LED technology can fully meet or exceed the incumbent mercury lamp.
While it is widely understood and accepted that UVC LED’s instant on-off capability offers a significant advantage and better alignment with actual consumer use than an “always on” mercury lamp system, a question remained whether an equivalent powered LED system could demonstrate equivalent disinfection performance as a low-pressure mercury lamp system. The experimental Klaran™ WR reactor was developed to demonstrate that UVC LEDs can achieve just this.
A standard Klaran™ WR was enhanced and modified to operate with the same power consumption level (6 W) as a comparable mercury lamp system (Fig. 2). Both systems were tested using water at a flow rate of 8 liters per minute (2.1 gallons per minute), with a UV transmittance of 97% at 265 nm and dosed with the addition of approximately 106 CFU/mL of E. coli, a common gram-negative, facultative anaerobic, rod-shaped bacterium, for testing.
As there is no established testing method for this type of comparison, Asahi Kasei devised the testing method and contracted an independent laboratory to perform the evaluation. Water quality samples recorded after 2 minutes steady operation with both systems were compared (Fig. 3), demonstrating how the Klaran™ WR had over 2 LRV(logarithmic reduction value) better performance than the mercury lamp system. Put another way, the Klaran™ WR system reduced E. Coli in the water to 1/100 of the level of the water disinfected by the mercury lamp system.